Combined air conditioning for heating rooms and improving of indoor climate
¹Institute of Technology, Estonian University of Life Sciences, Krutzwaldi 56,EE51014 Tartu, Estonia; *Correspondence: firstname.lastname@example.org
²Company AIRMAKER GTR, Riia 181A, EE51014 Tartu, Estonia
Geothermal equipment consists of intake air pipes, vacuum wards and undergroundconnecting pipes, placed near to a villa. The heat exchange ventilation equipment MENERGA191191 used in ventilation systems makes air inside the device circulate. This patentedequipment differs from the analogues of Germany, Japan, United States, etc. by the coolingexchange device. This device enables remarkable advantages in mounting and construction bydecreasing the length, installation depth and number of air pipes, simplifying and reducing themaintenance and increasing the equipment durability. The geothermal equipment is meant forcreating an environment with a constant temperature of 4 ºC and adjustable relative humidity inwarehouses and basements. It is for improving an indoor climate in villas’ basements,preheating, and air conditioning based on air heating as well. This equipment is indispensablewhen preheating greenhouses and cooling air in the hot season. The analysis of air climateparameters (temperature ϑk, relative humidity Ws, dew point ϑp, absolute humidity Wa,velocity v, oxygen content O2, carbon dioxide content CO2, positive light air ions n+, negativelight air ions n–) passing through the geothermal equipment is presented in the article. Heattechnical data (air specific heat capacity, characteristics of heat and cold exchange processes)are presented. This article summarises the research results of indoor climate qualities andpresents data about energetic-economical efficiency of the geothermal equipment (air specificheat and gross capacities, return air flow specific heat and gross capacities, the economic effectof pre-heating the villa and the post-heating expenses were analysed).